A required form completed by the applicant that provides an overview of their project.
Provide a written description of all work to be done. Show the location of all fixtures, existing and proposed, and identify the fixture type. Identify the use of each room. Show all equipment, duct and diffuser locations, and identify each zone. Note duct sizes and any penetrations through fire-resistive assemblies or protected areas. Locate all fire and/or smoke dampers if required.
Grease / Trap Interceptor Plans
Need calculations, 4+ fixtures requires engineered calculations, plans must show location of drain waste vent.
Show location of all fixtures, vents and clean-outs. Give sizes of all D/W/V pipe with lengths noted and type of material used. Note the Drainage Fixture Unit (DFU) for each fixture per UPC Table 7-3. Show locations of all water lines with pipe sizes noted and type of material used. Include the thermal expansion tank design used as required. Note the Water Supply Fixture Unit (WSFU) for each fixture per UPC Table 6-5.
Equipment / Fixture List
Provide a copy of the manufacturer's specifications noting the make, model, weight, and efficiency rating of each unit.